Traditional disinfection of newly installed or reconditioned pipelines involves filling the pipeline with a water and chlorus mixture, this is either dosed in or tablets are inserted into the pipe prior to filling. A soak time of 2hrs is required then the water must be flushed out and removed safely with no harm to surrounding areas or the environment. Using this system large quantities water are used on both during the ‘soak’ period and then the ‘flushing’.
The ESCS-PCS system reduces the amount of water significantly which in turn has a positive effect on the environment as well as having huge cost and time saving advantages.
This unique system incorporates the latest PLC computer control and embedded HMI display with bespoke spray head and atomising spray system. Our spray system monitors the PPL content in the water as it flows through the sensor, depending on the flow rate and pipe diameter it will automatically retract the spray head at the correct speed to gain the required theoretical thickness as desired by the client. All this information is recorded and printed real time using thermal printer. Also, the data is logged in the system which can be downloaded historically via a USB.
• COMPACT – TO FIT INSIDE VAN
• HOMOGENEOUS FOGGING ENSURES FULL DIAMATER COVERAGE
• REAL TIME MONOTORING
• BIO METRIC LOGIN FOR USER CONTROL AND QA
• NYLON BRUSH SKID ASSEMBLY ENSURES THE NEW COATING ISN’T COMPROMISED
• COST SAVING ADVANTAGES
• CONSUMER ADVANTAGES
Nzérékoré 150mm (6”) pipe 150m long
USING SODIUM HYPOCHLORITE (CHLORUS) TABLETS OR SOLUTION WATER REQUIRED TO FILL PIPE FOR 2 HOUR SOAK = 2650.20 LITRES
WATER REQUIRED TO FLUSH = 10,600.80 LITRES
TOTAL WASTE WATER = 13,251.00 LITRES PER PIPE
ALL ABOVE WATER NEEDS TO BE DISPOSED OF AND NEUTRALISED USING SODIUM THIOSULPHATE CRYSTALS
probably 150mm (6”) pipe 150m long
THEORETICAL THICKNESS 0.5MM USING SPRAY WITH HUWA-SAN TR50 WT
TOTAL WATER FOR 0.5mm = 35.2 LITRES
15 Minute soak period
RECONNECT PIPE TO NETWORK
NO FLUSHING REQUIRED
ANY ACCIDENTAL DISCHARGE WILL CAUSE LITTLE OR NO HARM TO THE WATER COURSE DUE TO THE FACT HUWA-SAN TR50 WT DEGRADES BACK TO WATER AND OXYGEN